PIPELINE INSULATING JOINT
Published：2017/08/01 Pipeline miscellaneous views：1518
PIPELINE INSULATING JOINT are used worldwide for permanently controlling the fl ow of electrical currents or
electrically isolating pipe sections in pipes and piping systems. Effective management of cathodic protection programs results from the use of these highly reliable substitutes for
fl anged insulating systems. Other benefi ts include protection against earthing currents at domestic and industrial premises, isolation of pipeline cathodic protection system, and to ensure that cathodic protection or stray currents do not cause increased corrosion.
PIPELINE INSULATING JOINTS shall be boltless and completely factory assembled in accordance with the
appropriate requirements of ASME, ASTM, API, DIN and BS codes.Insulation material is a thermosetting fi breglass epoxy material. NEMA G10/11. Sealing system shall be by two Standard “O” ring seals. Interior and exterior coating by epoxy with a thickness of 150 microns.
– Dielectric Resistance @ 5 KV
– Isolation Resistance > 50 MOhm
– Design According to ANSI/ASMEB31.3/4/8
– Dimens. ASME VIII Div.I